address: 3130 De Soto St
description_raw: Demo out the existing meter/panel/stem. Install a new 200 amp meter can with a 2" stem straight up with 2/0 copper feeder wires. Re-crimp the "hot" service drop to restore power to the service. Upgrade main ground system to code with a #4 ground wire from the meter can to an intersystem ground bar to 2 - 8' ground rods to water line and ensure gas and cold water lines are bonded. Install a 200 amp main breaker 42 circuit panel and correctly sized circuit breakers for existing "hot" branch wiring. Mark panel and breakers. I