address: 42 Gull St
description_raw: Demo out the existing meter can, install an underground only 200 amp single phase meter can left hand feed, right hand meter socket. Install a new main ground system including a number four ground wire from the new meter can through an intersystem ground bar to continue to terminate at 2 - 8 foot ground rods. Furnish and install a new 200 amp main breaker Eaton Cutler Hammer CH series 42 circuit panel and feed this new panel from the new meter can with 2/0 copper feeder wire.