address: 1331 Philip St
description_raw: The main electrical service is aged and incorrect. The wall behind the main service, which the electrical components are attached, is rotten. Will need to replace the main disconnect and the A/C 3-phase service disconnect, due to missing interior covers. In order to replace, one or two "Shut Down" days will need to occur.  This means we will remove the entire main service, customer to contact a carpenter/framer to rebuild the rotten wall, and once they are complete, we will furnish and install a new 200 amp, 3-phase electrical service with a new single phase 40 circuit main breaker disconnect, new 3-phase A/C disconnect, with a trough above both boxes to distribute power correctly. And adding 15 circuits for renovations and Knob and Tube rewire.