address: 13720 CREEKSIDE DR
description_raw: � Disconnect, reclaim refrigerant, make safe and remove two existing Carrier Cooling Only
  Condensers located to the east side of the house at ground level. One Condenser is 4-ton serving
  the basement level and one is 3-ton serving the second level.
  � Remove existing service power service disconnects they are old as the system and need
  replacement. Remove the existing power wiring and conduit from the old disconnects to the units.
  � Remove the existing thermostats. Remove two small Hydronic Heating units in garage and cap
  off piping and electrical.
  � Furnish and install tarps or laydown protection paper where required to keep from any water
  damage or leaking dirty pieces. Turn off Natural Gas from the Meter.
  � Shut down Boiler and Drain all heating water piping and boiler. Disconnect Boiler, flue piping,
  circulation pump and remove from the basement. Remove all water piping and old controls in the mechanical space in the basement as far back as possible and cap. Keep existing condensate
  piping though the wall. The PVC Back flow overflow drain shall remain intact and the Fan Coil
  PVC drain portion shall be eliminated from the drain.
  � Disconnect existing Duct connections connected to the two Hot Water Coils inside and remove
  the water coils, Fan Coils units, Support Stands, and Ducting not being used in reconnecting to
  new system. The determination of the ducting being removed will be explained during the
  demolition phase to the installation crew.
  � Dispose of all existing units and debris per EPA guidelines.
  � A new digital programmable 7-day thermostat shall be furnished and installed for each system.
  � Chemically Flush and pressure test existing refrigerant piping to be connected to new Air
  Condition systems. Replace where possible with new piping and insulation.
  � Furnish and install new 14+ seer 3-ton and 4-ton AC condensers in the same locations as the
  existing. The new condensers shall be installed on a new 2� pad.
  � Modify the existing duct connections to f