description_raw: Existing septic system to be abandonned and replaced to allow for a new building addition. The ex. septic tank is to be pumped, crushed, and backfilled. The ex. septic trenches are to be pumped as completely as possible.Dual alternating pump � Dual alternating pump system with alarm is required. Pump specifications are to be submitted to this office for approval prior to installation.Starting point of initial absorption system to be surveyed by a registered land surveyor. This property is in category W-6 and / or S-6 where there is no planned community service and an individual system may be installed on an indefinite basis without firm obligation to connect to community system when and if it becomes available. Trenches to be connected in series. &nbsp;Septic tank access port to be installed as per well and septic standards and specifications.&nbsp;No basement plumbing facilities by gravity flow.Trenches to be constructed on contour.Septic trenches to be 100 feet&nbsp; from any well location. Utilties must be 10 feet minimum from septic reserve area. Force-main to be 2-inch pvc. sch. 40. Septic tank to be 2-compartment; pump chamber to be top-seam 1000 gal. tank.
  
  &nbsp;