address: 111 GOODHILL RD, KENTFIELD, CA 94904
description_raw: Demo old NEMA 14/50 underneath the sub in garage.
  Install Wallbox with the existing 50amp wire and breaker.
  Program it to 40amps since it’s a continuous load. Permit fee and inspection included.  
  Install 20amp breaker for gate.
  Install wp GFCI for the gate circuit.